100KW / 125KVA Water Cooled Diesel Generator , 3 Phase Diesel
1. If you are interested in our products we sincerely invite you to
take a visit of our factory when you are in China. We can drive to
pick you up and visit our factory.
2. Suggest the best choice or referential suggestion based on
customers’ information. Answer all questions about the product from
customer.We will supply the best plan for you according to your
3. Build customers’ profiles, follow-up service, make regular calls
on customers,try our best to meet your demands.
4.24hours service on line,just the best service.
|1. Specification of genset|
|Dimensions(mm) (L×W×H)||1850X720X1250mm||Open type|
|2. Specification of diesel engine|
|Number of Cylinders||6|
|Cylinder arrangement||Vertical in-line|
|Aspiration||Turbo INtercooled, Air/Water cooling|
|Cooling System||Forced Water Cooling Cycle|
|3. Specification of alternator|
|Number of Phase||3|
|Connecting Type||3 Phase and 4 Wires|
|Number of Bearing||1|
|Exciter Type||Brushless ,Self-exciting, AVR automatic voltage regulating,|
100% Copper winding wire (Brush is also available)
|Telephone Influence Factor (TIF)||≤50|
|Voltage Regulation, Steady State||≤±1%|
|Transient State Voltage||≤-15%~+20%|
Installation requirements in machine room. Keep the machine room
clean.A dry,Inlet and outlet air is clear.The unit must exhaust the
air duct hood to prevent hot air from returning to the machine
room;Muffler shallMust be properly hoisted,To avoid crushing the
supercharger.When used in high dust environment,Not only in the
machine room to install filters and dustproofNets keep out excess
dust(unit water tank,Premature blockage of air filtration,Measures
should also be taken to prevent the dust from entering the exhaust
pipe.In the exhaust duct.
1.Select the oil that meets the requirements of the generator.
Before starting the engine, check whether the oil level and cooling
level are normalLocation, continuous boot operation4Check the oil
level around the hour.
2.Choose the antifreeze or antirust solution approved by the
manufacturer according to the ambient temperature.Add after
adjusting to proportion;Don'tUse clean water only (rusting of
engine channel, cavitation erosion, rust of thermostat, etc.).Add
cooling fluid to generate electricityThe machine body exhausts air
to prevent damage to the cylinder in the channel
3.The unit is forbidden to work under overload.The unit is strictly
forbidden to be hit by large load.
4.Before the unit is shut down, load is discharged and no load is
operated3 ~ 5Stop after a minute.The unit is not allowed to operate
for a long time under low load or idle state.The spare unit should
be operated without load at least once a month.Empty vessels
carryingTurn time10to15Minutes;And the annual load (80%At least
5.The power supply of the reserve unit should be charged regularly,
and the electrolytic level of the battery should be checked at the
same time. If not enough, it should be added in time (it can be
steamedBoiling water).Check whether the connection of the battery
line is firm. Do not connect the wrong way.
6.Operating personnel carefully complete the unit's operation,
1.Unit operation200to300Oil must be changed every hour or every
year. Oil must be removed at the same timeDevice (including
bypass).Oil should be used for the first time or under harsh
conditions100Change within hours.
2.The engine's air filter is available500Change in an hour or
two;More dust and other harsh environmental conditions will be
greatly reducedThe cycle of empty filter, observe the position
indicated by the empty filter blocker, indicate that it must be
replaced when entering the red area.
3.The coolant is replaced every two years, and the coolant filter
should be replaced annually.
4.The quality diesel must be chosen in line with national
standards.The first care should be cleaned regularly, with fine
aluminum for each use500Hours should be replaced.With oilWater
separator unit each use50Drain or replace the filter element
regularly around the hour.
5.Never reuse the engine after cleaning.Select pure engine filters
Pakcing and delivery:
1. What's the power range of diesel generator?
Answer: Power range from 18-2000kw,23-2500kva.
2. What's the delivery time?
Answer: in 10 days after get the deposit.
3. What's the payment term?
Answer: we accept T/T,and 30% T/T as the deposit,the balance should
be paid before delivery.
irrevocable L/C at sight.
4. What's your warranty?
Answer: 1000 working hours or 1 year whichever comes first.
5. What's your MOQ?
Answer: 1 set
6. What's the frequency of diesel generator set?
7. What's the voltage of your diesel generator set?
Answer: the voltage is 220/380V,230/400V,240/415V or as your