Fiberglass Water Tank
SMC water tank is also called SMC storage tank, FRP/GRP water tank,
SMC panel tanks. It is a new type of tank. It is made of high
qualified SMC panels. Sheet molding compound (SMC) is a kind of
fiberglass reinforced plastic, which is a mixture of unsaturated
polyester resin with impregnating augmentation material, filling
material and glass fiber. SMC water tank is nontoxic, durable,
lightweight, corrosion resistant and good-looking. Meanwhile, it's
easy to maintain and long-life. It is widely used in water storage
in residential buildings, schools, hotel. SMC water tanks are used
both for domestic water as well as medicine and health where needs
good water supply quality.
Sectional Water Tank Specifications
1.SMC moulded singal board specifications(If need other
specifications we can chatting)
1000x1000mm ,1000x 500mm ,500x 500mm
2.thickness:5mm, 8mm, 10mm ,12mm, 14mm,,16mm ,The thinkness is 5mm
signal board is used for water tank cover plate
3.SMC moulded water tank is measure up GB5749-85
4.Capacity: 0.125m3 ~ 5000m3
SMC moulded signal baord specifications
|Tensile strength Mpa||≥70MPa|
|Bending strength||≥100 Mpa|
|Water absorption||≤ 1.0%|
|Fiber glass content||≥25%|
|Flexural Modulus of Elasticity||≥ 5900MPa|
1 Based on the first plane leveling cement, on the same plane so
that the error should not exceed ± 0.5cm.
Welding channel: channel according to the size of the tank welding
good match its size and the tank floor size, channel steel welding
complete, the diagonal measurements, error of ± 0.5cm, and all
welds to connect uniform row seam line.
2 Install the end state: water tank according to the board printed
number and description of the arrangement, the connection of the
tank bottom, while between two boards add sealing tape, bolted ¢
10's. Securely sealed bottom plate, bolt afterburner afterburner to
a uniform, one-time can not be too much force, otherwise due to
uneven force caused by the split plate phenomenon.
3 Is connected with a fixed angle iron and channel steel base
plate, so that the tank housing more firmly fixed on the basis of
4 Install states: water tank according to the board printed number
and description to identify the layers BOND NO tank state body, and
previously separate state body assembled with bolts.
5 Install stretch: Stretch inner tank according to the size, number
and find internal reinforcement length. Measuring stretch of wire
reinforcement plate fastening parts, Indian painting, drilling, on
to the wire, tighten to make a flat stretch in balance with the
tank housing. If there is a large error between the casing and
reinforcement, can be adjusted by adjusting the size of the error
bolt tightness, until the error is adjusted to a minimum so far.
6 Install the cover: the final installation of the tank top cover,
and even fastening bolts can not force too large or too small.
After all the fasteners tank adjusted, according to the drawing
hole location, a good all pipes, having a good valve flange for
7 Tanks fully installed, unified inspection, adjustment, test the
water does not leak in compliance.
How to correctly use fiberglass tanks?
1. Fiberglass tanks for the storage of drinking water at room
temperature and the design and manufacture, please do not store hot
water and other liquids (chemicals, oil, etc.)
2. On-site construction: pre-construction, install the stay
requested by the foundation. Providing power and construction
inspection seal with water.
3. To avoid water tank next to the fire: When welding operations,
to take protective measures, not to splash the water tank panels
4. To prevent contaminants from flowing into the tank from the
outside: for the convenience and safety of maintenance and
inspection, the tank must leave some space around.
5. The molded fiberglass boards do not touch on the corners, do not
beat something with hard tools.
6. In order to prevent expansion of the pipe, shrinkage, partial
load and shock, glass steel water tank, outlet pipe must be of
rubber around the streets (expansion joints), to take over the
additional weight should be supported, not acting on the tank.